Sodium Hypochlorite is available as solutions in varying strengths. Concentrated solutions for disinfection purposes may contain 10% to 18% available chlorine while domestic and laundry bleaches typically contain 3% to 6% available chlorine. United States Plastic Corp does not recommend our polyethylene tanks for concentrations above 16.5% and concentrations between 12% and 16.5% should not be used at elevated temperatures.
Polyethylene is not actually affected by just sodium hypochlorite, it is however effected when the sodium hypochlorite is contaminated. Causes of contamination can be trace amounts of metals from pumps, plumbing, and fittings or poor quality sodium hypochlorite. This contamination will cause accelerated deterioration of the tank over a period of time. Deterioration will manifest as brittleness and stress cracking. Sunlight will accelerate the rate of the attack.
We recommend polyethylene tanks used for sodium hypochlorite to be heavy walled or preferably crosslinked. If used outdoors tanks should contain a UV inhibitor to minimize damage.
Title: Sodium hypochlorite and its effects on polyethylene.
Description: Recommendations on tanks for sodium hypochlorite.
The information contained in this article is for general information purposes only. The information is provided by
United States Plastic Corp. and while we endeavor to keep the information up to date and correct, we make no representations or
warranties of any kind, express or implied, about the completeness, accuracy, reliability, suitability or availability with
respect to the website or the information, products, services, or related graphics contained on the website for any purpose.
Any reliance you place on such information is therefore strictly at your own risk.
In no event will we be liable for any loss or damage including without limitation, indirect or consequential loss
or damage, or any loss or damage whatsoever arising from loss of materials, time or profits arising out of,
or in connection with, the use of this information.